Scope of Works
API was recently contacted by a water utility client in the UK. The utility had identified a leak on a 1200 metre section of 1000mm DI pipeline. The pipeline had been tested over a period of 18 months and would not hold pressure above 10 bar. The pipeline was installed in wet ground conditions and the pipe was located close to marshland in a water treatment work area. Due to the pipeline bury depth and location, the client tried using traditional techniques using several specialist leak detection companies; however no company could pinpoint the leaks location, which created several dry dig excavations, along with a very expensive delay to the project.
The pipeline is a water treatment outlet main and deeply buried.
The pipeline is a 1000mm pipe with 16 bar pressure test required, and was installed over 18 months ago.
The client utilised several ‘specialist’ leakage teams and searched for leaks over several months with the following methods:
Noise correlators – no leaks identified (not accurate on large diameter metallic pipes)
Listening stick- Pipeline was deeply sited below ground so this technique not feasible
Tracer gas – ground structure and conditions resulted without any results
Temporary bypass and flowmeter- this identified a leak, however does not pinpoint its location
This had a major knock on effect, as the client cannot proceed with a localized repair solution, and also may require a road closure at the treatment works entrance.
Commissioncam HD CCTV Assessment tool
2000m Pipepod Hydrostatic system on site
PIPA uses technology that includes a pressure rated camera (CommissioncamTM) and hydrophone capsule (PipepodTM) tethered to a 2000m cable to give the operator video and recorded audio data during an inspection. The system enters a pipeline via an 80mm to 150mm riser; the system works on a live or pressurised basis, and can cover a distance of up to 2km per day.
The cable is installed using a tethered swab; once the cable is installed the sensors are rated to 20 bar and offer pipe installation companies a fail-safe when pipe issues occur:
The Pipepod sensor accurately detects leak location in all pipe materials including plastics
The HD camera sensor inspects pipe condition to offer a quality control system to check the pipe has been correctly cleaned
The pipe is free of air pockets
Check gasket and joint alignment
The technology is the only long range new main inspection system on the market being fully battery powered and only requires a 2 man team for its implementation.
Video stills of survey findings
Leak identified on wide open joint section with debris ingress identified
HD CCTV still showing joint and cement lining
Every pipe joint was inspected under pressure
Pipeline was free of any other leaks
PIPA successfully identified the leak at 413 metres
Tethered insertion technology system allowed for precise location of the leaks to be identified
Acoustic system is very sensitive and able to pick up small and large leaks
Operator was able to identify no other leaks with joints identified in close proximately to each other
Camera system was used post pipe repair to validate the pipe was clean and free of debris
It would have been very difficult and expensive for contractor to find the remaining issues within the water main. The CCTV and acoustic capability proved indispensable for locating issues and trouble shooting.
PIPA completed the inspection in 1 working day, and in total successfully identified and located 1 leak (now verified).
The contractor resolved the ongoing issue by removing the guess work at a fraction of the cost and time they invested in other methods in previous months.
The client estimated a capital spend of £250,000 GBP was invested in the project prior to the Pipepod Hydrostatic and Commissioncam being used.
API-PIPA representative said- The project was a great success, Ideal due to pipe location and material and also a great case study for our company. The contractor had exhausted all other pipeline inspection avenues, and was more than relieved when we offered a solution.
The Pipepod and Commissioncam system removes any delays on all new pipe installation projects, installing our unique cable as part of the swabbing procedure is a game changer for the industry!
PIPA has also delivered successful projects with the majority of the UK water utility companies, and now offers its technology along with training all over the World.
“Having a supply of water, and a portable-powered rig means that we are self-sufficient on site”, says Mike Hall, SVI’s Contract Development Manager. “And because the rig is compact enough to be operated from the back of our vehicles, we are able to continue working even when it rains”, he adds.